Besta Bamboo Machine Co.,Limited
Mob: +86-18657106860 (Whatsapp)
Fax: +86-571-8213 3126
Wechat ID: ilikechanging
Add: Tangpu Industrial Park, Anji County, Zhejiang Province
1, the boiler factory should be accompanied by "Safety technical specifications required by the design documents, product quality certification, safety and use of maintenance instructions, supervision and inspection certificate (Safety performance supervision and inspection certificates) ".
2, boiler installation, maintenance, transformation. Units engaged in the installation, maintenance and transformation of boilers shall obtain the qualification certificate for installation and maintenance of special equipment issued by the provincial Bureau of Quality and technical supervision, so as to be engaged in the installation, maintenance and transformation of boilers.Construction units in the construction of the proposed installation, maintenance, transformation of the situation in writing to inform the municipality or the jurisdiction of the special equipment Safety supervision and management department, and will be informed to send the local county quality and technical Supervision Bureau for the record, after the notice can be construction.
3, boiler installation, maintenance, transformation of the acceptance. After the construction of the construction unit to the Quality and Technical Supervision Bureau of Special Equipment Inspection of the boiler's hydraulic test and installation supervision and inspection.Qualified by the quality and Technical Supervision Bureau, Special Equipment Inspection Institute, county Quality and Technical Supervision Bureau to participate in the overall acceptance.
4. Registration and registration of boilers.After the boiler acceptance, the use of units must be in accordance with the "Special equipment registration and use management rules", fill in the "boiler (census) Registration registration Form", to the quality and Technical Supervision Bureau registration, and apply for the "Special Equipment safe Use registration certificate."
5, the operation of the boiler.Boiler operation must be trained and qualified to obtain the "Special Equipment Operation personnel Certificate" of the Licensed personnel operation, the use must strictly abide by the operating procedures and eight systems, six records.
6, the inspection of the boiler. Boilers are regularly inspected once a year, and boilers that are not regularly inspected by safety are not allowed to be used.The safety accessories of the boiler are regularly inspected once a year, the pressure gauges are verified semi-annually, and safety accessories that are not regularly inspected shall not be used.
7, it is strictly forbidden to install atmospheric boiler as a pressurized boiler for use. It is strictly forbidden to use water level meter, safety valve, pressure gauge three safety accessories incomplete boiler.